Air conditioning vacuum pump is used to remove unwanted air and water vapor from the air conditioning system when it is under service. When the air conditioner needs to be repaired, the first step taken is usually to recover the refrigerant from the system for reuse later.
Once the recovery job has been done, you can now proceed to do the necessary troubleshooting and repair work. The next step is to check and make sure that the system is leak free else steps will have to be taken to rectify this.
The evacuation process is the next step in which the vacuum pump is used to remove the air and moisture from the refrigerant system. Once this is done, the charging process can be carried out before doing a full test on the system.
In a refrigerant system, only the refrigerant and oil should be circulating. During servicing or after many years of operation, the air may enter the system. The air from the atmosphere that enters the system include oxygen, nitrogen and moisture. These unwanted components will cause:
In order to remove all the unwanted moisture and gases from the refrigerant system, a state of near vacuum has to be achieved in which the pressure in the system is forced to go below the atmospheric pressure. The absolute value of the atmospheric pressure at sea level is given by 29.92 in. Hg or 14.696 psia or 759.999 mm Hg or 759,999 microns.
In the typical system, the vacuum pump is required to create a vacuum state of about 300 to 500 microns. An electronic vacuum gauge is needed to measure the level of vacuum in the system. Check the specifications of the vacuum pump and make sure that it is able to achieve the vacuum state as required by the manufacturers of the equipment.
A 2-Stage Vacuum Pump from Robinair
Rotary compressors are used in the pumps and the better ones that are able to produce the lowest vacuums are the 2-stage rotary vacuum pumps. However, they are more costly but their abilities to remove moisture effectively is one of the main reasons why many technicians prefer to purchase this model.
As the system enters low vacuum state, the moisture will begin to boil and becomes vapor enabling its removal from the system easily.
Proper oil needs to be used when operating the air conditioning vacuum pump. Use only the recommended oil to enable the pump to achieve the specified vacuum state.
Take note of the followings when selecting air conditioning vacuum pump.
Popular brands in the market include Robinair, Yellow Jacket, Inficon and Arksen.
Visiting HVAC events and trade shows are one of the best way to equip yourself with the latest happenings in the air conditioning and refrigeration field. See the listing of events for year 2017-2018.
Direct Expansion System uses components such as the compressor, evaporator coil, metering device and condenser coil to expand the refrigerant and cool the room.
Zigbee is another standard wireless option to control the air conditioners in homes or buildings.
Here are the air conditioners frequently asked questions and answers.