Most of the big buildings and offices these days are air conditioned using central air conditioner. Most of us would probably not notice it as the conditioned air is ducted to the space or rooms and what we see is only the diffuser and a tiny themostat that controls the temperature of the room.
The bulk of the equipment are located in the plant room and air air handling unit room (AHU Room). There are basically two types of systems that are being implemented in most buildings. They are the Direct or the Indirect type.
The Direct type is also known as the DX system where the air in the space is directly cooled by the evaporator coil. The air from the space to be cooled is circulated over the cooling coil of a refrigeration plant.
The Indirect type uses chilled water or brine from the refrigeration plant that is circulated through the cooling coil which is located in the air-handling unit (AHU) to cool and dehumidify the room air. This system is also known as the central chilled water system.
DX Central Air Conditioner System
In DX system, the condensing unit where the compressor and its motor as well as the condenser are located in the Plant Room, separated from the space that is to be conditioned and the air-handling unit. The condensing unit should be located as close as possible to the AHU to keep the pressure drop in the piping to a minimum. The compresssor can be of open type or semi-hermetic type. The open-type can be directly or belt driven by a motor or engine.
The AHU is located in another room. It consists of evaporator coils, air filter, return air duct, fan motor, themostatic expansion valve and ducting works to the space to be conditioned. The return air-duct and supply air-duct are insulated.
The suction and liquid lines connect the condensing unit to the cooling coil.
In the water-cooled system, the condenser is water-cooled and is fitted to a steel framework on which the compressor and the motor are mounted to form a compact condensing unit.
Chilled Water(CW) System
In the chilled water system, the compressor and its motor, the water-cooled condenser and the chiller (evaporator) are all assembled in a huge structured steel framework. It forms a complete and compact refrigeration plant known as a chiller package. The refrigeration piping, thermostatic expansion valve, liquid line solenoid valve and line shut off valve are all compacted together.
The huge chiller.
Visiting HVAC events and trade shows are one of the best way to equip yourself with the latest happenings in the air conditioning and refrigeration field. See the listing of events for year 2016-2017.
Inverter Air Conditioning is the latest technology available in HVAC industry. Use this technology for comfort and better energy efficiency
Variable Refrigerant Flow or Variable Refrigerant Volume system is the best solution to be installed in commercial buildings as it is highly energy efficient and flexible.
Here are the air conditioners frequently asked questions and answers.