Fan speed controller or low ambient fan controller is a control that is used to control the fan speed of the air-cooled condenser in a heat pump direct expansion system. Heat pump is used in temperate countries and can be used to operate in cooling or heating mode. When used as a heating mode in winter, the indoor coil acts as a condenser and outdoor coil as evaporator.
When the unit is set to cooling mode in summer, the indoor coil will operate as an evaporator and the outdoor coil as condenser. This is accomplished by the use of a 4-way-valve that reverses the flow of the refrigerant in the system. In the United States, usually when the reversing valve is ON, the system will operate in cooling mode and when it is OFF, in heating mode.
When the outdoor ambient temperature is low such as 50°F(10°C) or below, we will usually want to run our heat pump in heat mode to heat up the room to maintain a comfortable temperature for the human body.
However, there are instances in which we want to operate the heat pump in cool mode even though the outdoor surrounding temperature is low. These places may include the followings.
If we continue to operate the heat pump in cooling mode, the head pressure will drop. The expansion valve needs a certain head pressure to operate properly and if the head pressure continues to drop, it will cause the air conditioning system to stop operating. As a result, the evaporator will freeze-up and compressor slugging will occurred.
Compressor slugging is caused by the entry of liquid refrigerant into the compressor's cylinder during operation. It will damage the valves, bearings and other mechanical parts of the compressor.
A low ambient head pressure control from ICM Controls
The solution to this problem is to install a fan speed controller that will be able to regulate the speed of the outdoor fan of the condenser. In order to use the controller, check the specifications of the fan to ensure that the fan is able to be modulated by changing the supply voltage to it.
A sensor will be mounted on the liquid line of the condenser where its temperature is used to control the speed of the fan. By regulating the speed, the head pressure will not drop too low hence the heat pump will still be able to operate in cooling mode even though the outdoor ambient temperature is low.
Look and compare the features of a fan speed controller before buying it.
Here are some of the common HVAC Questions that most users of air conditioners or heat pumps asked.
I have a 1Hp 230VAC 60Hz National split type wall mount room air conditioner. It's been working well for quite few years now. Recently I experienced the
If your air conditioner freezes up during operation, here are some of the steps you can take before calling a technician to service your equipment.
Visiting HVAC events and trade shows are one of the best way to equip yourself with the latest happenings in the air conditioning and refrigeration field. See the listing of events for year 2018-2019.