Electronic solid state phase protector has been around for some time now with the advancement in the semiconductor technology. It has enabled the design of this device that is used as part of the motor controls. They are accessory devices that designers used to protect the motors from premature failure due to voltage faults.
In the field of HVAC, these devices are used to protect large three phase fan motors and compressor motors from being damaged.
Check the specifications for the features that are being offered as they varies from one manufacturer to another. Here are some of them that you will want to consider.
Undervoltage & Overvoltage
Motors operate the best when the input voltages are within the specifications with a small tolerance. Undervoltage will reduce the torque in starting up the motor, increase in current flow and eventually causing heat to build up in the windings. This will cause the insulation of the windings to breakdown hence decreasing the lifetime of the motors.
When overvoltage occurs due to a fault in the incoming power supply, the motor will go into saturation causing high current to flow and eventually damage the windings of the motors.
Check that the devices are able to protect the motors when this happen.
The three-phase motors will rotate in the reverse direction when the phases of the power supply are reversed. This will cause improper operation to the compressors in particular the rotary, scroll and centrifugal compressors. Having this protection is necessary in the design of these systems.
All the three phases to the motor must be present or else it will overload. If one phase is loss, the device will stop the power to the motor and alert the user through the indicators on the phase protector.
It is always necessary to ensure that there is a certain minimum duration that has elapsed before the motors can start again. This is critical for large motors as it is usually not designed to restart immediately. A time duration of a few minutes is usually recommended by the manufacturers or the designers. Having this feature in the device will help to ensure the lifetime of the motor is protected.
When the 3-phase power supply voltage from the utility company is not balanced or an unbalanced happens that is caused by the load in the building, it will cause the motor to overheat and damage the windings.
The imbalance voltage usually can be set and the recommended value is usually below 2%.
Here are some of the common HVAC Questions that most users of air conditioners or heat pumps asked.
I have a 1Hp 230VAC 60Hz National split type wall mount room air conditioner. It's been working well for quite few years now. Recently I experienced the
If your air conditioner freezes up during operation, here are some of the steps you can take before calling a technician to service your equipment.
Visiting HVAC events and trade shows are one of the best way to equip yourself with the latest happenings in the air conditioning and refrigeration field. See the listing of events for year 2018-2019.